You have no items in your shopping cart.
Capacity : 36,000-45,000 grains
Service Flow Rate: 12 gpm
Backwash Flow Rate: 2.4 gpm
Iron Removal: 2 ppm
Operating Temperature Range: 34 to 110ºF (1 to 43ºC)
Operating Pressure Range: 20 to 120 psi (1.37 to 8.27 bar)
Resin Volume: 1.5 Cubic Foot
Mineral Tank Size: 10" x 54"
Brine Tank Size: 18" x 36" with fittings
Brine Tank Salt Capacity: 325 Pounds
Mineral Tank Color: Black
Brine Tank Color: Black
Float Valve: Yes
SFT-150DM-WF Water Conditioning Instructions:
1) Fill Vortech Mineral Tank with Resin. (Riser tube is already installed.)
a. Remove tank from carton.
b. Make sure riser tube is properly connected to Vortech plate.
c. Place funnel (provided) on top of tank.
d. Pour resin or media into mineral tank.
e. Remove funnel.
f. Remove tape from the red protective cap, used to seal the riser tube. Discard tape and cap.
2) Control Valve Installation.
a. Remove valve and components from carton.
b. Lubricate distributor and tank 0-ring.
c. Install upper Basket onto valve.
d. Install bypass on valve.
e. Install valve on mineral tank.
3) System Assembly.
a. Place system in a sheltered area, so it will not be exposed to rain or weather.
b. Connect incoming water to inlet of valve.
c. Connect house supply line to outlet of valve.
d. Connect 5/8" drain tubing to valve and drain.
e. Connect 3/8" tubing to valve and brine tank.
a. Complete "start-up" settings.
b. Follow other directions in Manual (provided).